Why do we store gas
Underground gas storage facilities enable:
- balancing supply and deliveries of gas through gas storage surplus during periods of reduced demand and its return in situations of fuel demand growth,
- ensuring stable operation of gas fields by injecting natural gas that is being produced, regardless of the current market demand for this fuel,
- ensuring stable functioning of a gas transmission system due to satisfying storage capacity needs of the Transmission System Operator,
- establishing and maintaining mandatory natural gas reserves in accordance with the Act on Fuel Reserves,
- optimizing the transactions for purchase and sale of natural gas for its price volatility,
- ensuring security of gas supply (the ability to execute contractual obligations at a relatively constant volume of purchasing contracts and variable customer demand for natural gas),
- fulfilling the obligations to purchase the minimum quantities of natural gas at a specified period of time (take or pay obligation),
- providing support for wind energy by enabling delivery of electricity being produced on the basis of natural gas during periods when the wind is not blowing with the adequate force.
Gas storage history in PolandThe history of underground natural gas storage in Poland started in 1954 in partially depleted gas deposit Roztoki located near Jasło.
UGS Roztoki was the first underground gas storage facility in Poland and one of the first in Europe.
The rapid development of UGS in Poland started in 1979. That was the time when operation of UGS Brzeźnica and UGS Swarzów was initiated. Subsequently, the operation process included the following facilities: UGS Strachocina, UGS Husów UGS Wierzchowice, CUGS Mogilno and CUGS Kosakowo.The years when individual underground gas storage facilities in Poland were being included in the operation are shown below.
|1954||gas storage in a depleted gas deposit Roztoki near Jasło, UGS operation in the years 1954-1963 and 1976-1980|
|1979||UGS Brzeźnica, gas injection commenced in June|
|1979||UGS Swarzów, gas injection commenced in July|
|1982||UGS Strachocina, gas injection commenced in May|
|1987||UGS Husów, gas injection commenced in October|
|1995||UGS Wierzchowice, gas injection commenced in May|
UGS Roztoki - first industrial attempts to store gas in partially depleted natural gas field in Europe
UGS Roztoki was located in what currently is the Podkarpackie voivodeship in the Jasło region. Geographically, the area is located in the valley of the Jasiółka river within the area of Jasielsko-Krośnieńska Valey, being a part of Pogórze Środkowobeskidzkie.
Information about the deposit
The deposit of high-methane natural gas and crude oil Roztoki-Sądkowa was discovered in 1922. The original recoverable reserves were documented in the volume of 692 million cubic meters of gas.
The operation of the deposit began in 1931 and lasted continuously until 1954. Then due to the decision to build the UGS facility, the gas production was stopped and the process of gas storage began. The degree of exhaustion of the primary recoverable reserves in 1954 amounted to approximately 92%.
The oil and gas deposit at the Roztoki – Sądkowa block, which was used for storage, developed within the Potok fold in the formations of the Silesian nappe. The bed level is the second horizon of Eocene Ciezkowice Sandstone. There is a zone of gas and oil in the bed. They are supported from the floor by not very active reservoir water of surrounding and underlying character. Storage level is insulated from the top and bottom by the layers of Hieroglyphic and variegated shales.
Basic parameters of the storage horizon:
|Average effective thickness of reservoir rock [m]||60-80|
|Average geophysical porosity of reservoir rock [%]||14|
|Average geophysical permeability of reservoir rock [mD]||55|
|Original static bottom-hole pressure in the reservoir horizon [MPa]||11,38|
|Depth of the reservoir horizon top [m]||1100-1300|
Information on the Storage facility:
|The start year of UGS operation||1954|
|The end year of UGS operation||1980|
|Working volume [million m3]||35,50|
|Static wellhead pressure [MPa]||1,27-2,95|
Methods of natural gas storage
There are many ways of storing natural gas but the most popular one uses underground storage facilities.
Three main types of underground gas storage facilities are found:
- in partly depleted oil and gas reservoirs,
- in aquifers,
- in salt caverns
Natural gas may also be stored in:
- decommissioned mine excavations,
- rock caverns,
- overground tanks
The following chart presents the share of different types of storage in the total storage working volume worldwide:
Storage in partly depleted reservoirs
The majority of UGS facilities are located in partly depleted oil and gas reservoirs.
Advantages of storage in depleted reservoirs:
- Usually there are existing connections with major gas pipelines.
- Wells and surface facilities already existing in the field can be utilised, which significantly reduces the construction cost.
- Reservoir geology is well recognised. A reservoir forms a geologic trap, which minimises the risk of uncontrolled gas leakage from the storage.
- Unproduced indigenous gas may be used as a gas cushion, which reduces the investment expenditures.
Disadvantages of storage in depleted reservoirs:
- Usually facilities of this type are capable of running only one injection/withdrawal cycle during a year.
- The wells and overground infrastructure of such fields is usually relatively aged and requires costly reconstruction and maintenance.
The first storage facility of this type was built in 1916 in the State of New York in the USA.
The picture below shows a visualization of an underground gas storage facility in a depleted reservoir:
Storage in aquifers
There are many underground gas storage facilities located in aquifers. Such structures may be used for underground gas storage when the aquifer stratum is covered by impermeable rock stratum and forms a trap. The geology of aquifers is similar to that of partly depleted hydrocarbon reservoirs but the construction of underground gas storage normally requires a larger gas cushion to be formed and more detailed monitoring of the gas injection and withdrawal process. Also, no existing technical infrastructure, such as wells, pipelines, dehydrating installations, compressors, etc. is available in this case. Comparing to installations in depleted reservoirs, UGS facilities in aquifers may require more powerful compressors and more efficient dehydrating equipment. On the other hand, owing to the presence of water, the pressure in such facility is higher which results in the possibility to achieve higher gas withdrawal rates. This is particularly important in case of a sudden need to deliver large volumes of gas to the grid.
Advantages of storage in aquifers:
- Usually located in close proximity to final consumers.
- Relatively high withdrawal rate.
- Better capability of running multiple cycles in one season as compared to storage in depleted reservoirs.
Disadvantages of storage in aquifers:
- High geological risk. A structure of this kind did not contain hydrocarbons in the past, which means that there is some uncertainty as to the tightness of such facility.
- Higher operating costs related to extraction of water.
- Need to create a large gas cushion.
Storage in aquifers was used for the first time in 1946 in Kentucky (USA). The majority of storage facilities of this kind are operated in the United States, France and the territories of the former Soviet Union.
Visualisation of underground gas storage in aquifer:
Storage in salt caverns
Storage facilities located in salt caverns are characterised by very high injection and withdrawal rates in relation of the working volume. They occupy much smaller space than other types of storage. This results in much easier facility monitoring and operation. Also, the construction time is shorter. The development of salt caverns, calculated in relation to the achieved working volume, is however more costly than in case of depleted hydrocarbon reservoirs or aquifers. On the other hand, the facilities of this kind may run multiple injection and withdrawal cycles during one year, which greatly reduces the cost per unit of gas stored. Despite the fact that this type of storage is most expensive as regards both the construction and maintenance, it provides a very good security in case of a sudden growth of demand for natural gas. It is also more useful in regulating short-term fluctuations, both on national and local scale.
Advantages of storage in salt caverns:
- Small share of buffer gas in the total storage volume.
- Very high injection and withdrawal rate (much higher than in case of storage in depleted reservoirs and aquifers).
- Capability of running multiple injection and withdrawal cycles during one year, which enables the balancing of smaller fluctuations of natural gas supply and demand (e.g. daily).
- Low risk of untightness.
Disadvantages of storage in salt caverns:
- High investment expenditure required for construction of such storage facilities.
- High operating costs.
- Limited options for utilisation or disposal of brine produced during cavern leaching.
- Loss of working volume as a result of convergence.
This type of storage facility was used for the first time in 1961 in Michigan, USA.
Visualisation of underground gas storage in salt caverns:
Energy security and Undergroound Gas Storage facilities
The demand for natural gas in Poland is covered from two sources:
- extraction of gas from indigenous fields - about 30%,
- import of natural gas - about 70% (Russia is the main supplier).
Sources of domestic natural gas supplies have a delimited capacity resulting from geological and deposit conditions, the number of wells and operating parameters.
Deliveries of imported gas are usually at the stable level resulting from the execution of agreements and technical parameters of transmission network. As regards imported gas supplies there are also some periodic risks due to political reasons.
Moreover, in our climate there are significant air temperature differences between the summer and winter seasons, which causes periodic fluctuations in the demand for natural gas for heating purposes.
Due to the ability to maintain mandatory and trade reserves of natural gas, Underground Gas Storage facilities play a crucial role in ensuring the energy security of the country. They also increase the energy independence of our country in the periods of peak demand for natural gas.
Gas Injection to and Withdrawal from a UGS Facility
Gas injection from the transmission pipeline to the UGS facility
The injection of gas to the storage facility takes place as follows: gas from transmission pipeline (9) flows through strainers (8) which capture any solid or liquid impurities, and then passes to the custody transfer section (7). After the measurements are taken, the natural gas stream flows to the gas compressor station (5). After compression, the gas is transported to coolers (6) in order to be cooled down. After the cooling, the gas is sent to the gas distribution station (3). From the distribution station the gas flows to individual wells (2) through which it is injected to the storage reservoir or the cavern (1).
Gas withdrawal from the UGS to the transmission pipeline
During the withdrawal gas from individual wells (2) is fed to the gas distribution station (3), and then to the gas dehydration installation (4). After the dehydration, the gas stream flows to the gas compressor station (5). Following the compression, the gas is passed through gas coolers (6) to the custody transfer section (7). Once the measurements are taken, the gas is delivered to the transmission pipeline (9).
Gas injection from the transmission pipeline to the UGS in a non-compressor system
The injection of gas to the storage facility takes place as follows: gas from transmission pipeline (9) flows through strainers (8) which capture any solid or liquid impurities, and then passes to the custody transfer section (7). Once the necessary measurements are taken, natural gas flows to the gas distribution station (3) and then it flows to individual wells (2) through which it is inject to the storage reservoir or a cavern (1).
Gas withdrawal from the UGS to the transmission pipeline in a non-compressor system
During the withdrawal gas from individual wells (2) is fed to the gas distribution station (3), and then to the gas dehydration installation (4). From this point, the gas is sent to the custody transfer section (7). Once the measurements are taken, the gas is delivered to the transmission pipeline (9).
Examples of Well Schamatics and Core Pictures
Core - a cylinder-shaped piece of rock obtained as a result of drilling through rock formation by the means of a coring bit. Cores are taken from boreholes during engineering geology studies with a view to understanding the geology of the area. They enable, among other things, accurate determination of the rock types and dip.Samples of cores collected during the drilling of production wells in the underground gas storage facility: Typical completion of a UGS well developed in salt caverns: Example of wellbore design in the Underground Gas Storage Facility developed in a partly depleted natural gas deposit: Example of storage cavern geometry: Example of storage cavern geometry:
Salt Deposits in Poland
The territory of Poland offers suitable geological and mining conditions for the design and construction of large-scale underground hydrocarbon storage facilities in halite deposits. Halites are found within two saline formations, i.e. Upper Permian (Zechstein) and Neogene (Miocene). Due to their extent and geological and tectonic considerations, the most favourable conditions for the development of underground gas storage facilities exist within the Zechstein saline formation. In this formation, halites are present in diapir or stratiform-type deposits.
In Poland, eleven diapir deposits (Wapno, Damasławek, Góra, Mogilno I, Moglino II, Lubień, Łanięta, Kłodawa Północ, Kłodawa Centrum, Kłodawa Południe, Rogóźno) and six stratiform deposits (Łeba, Mechelinki, Zatoka Pucka, Kazimierzów – Sieroszowice, Rybnik – Żory – Orzesze, Bytom Odrzański) have been discovered.
Due to their geometry, diapir rock salt deposits have a limited horizontal extent (up to several kilometres) and very significant vertical penetration (up to several thousand metres). Because of their geological history diapir deposits typically have a complex internal structure.
Stratiform salt deposits have a vast horizontal extent but a limited thickness. The structure of stratiform halite deposits is relatively simple as the beds run horizontally or are slightly inclined and moderately disturbed. The bed thickness varies within the range from 200 to 300 metres.
Map showing the location of diapir and stratiform halite deposits and prospective deposit areas
for the development of underground gas storage
- Autumn Maintenance Downtime Period
- Bundled Unit
- Capacity Allocation (PP)
- Emergency Situation
- Firm SSA
- Gaseous Fuel
- Injection Capacity
- Long-Term SSA
- Network Code
- Secondary Market
- Weekly storage service